Understand the Safety Requirements for Wiring Pool, Spa, and Sauna Equipment in California
The U.S. Consumer Product Safety Commission (CPSC) recommends installing and using ground-fault circuit-interrupters (GFCIs) for protection against electrocution hazards involving electrical circuits and underwater lighting circuits in and around pools, spas, and hot tubs.
While grounding provides essential protection for pool, spa, and hot tub equipment, GFCIs are the most effective means for protecting people against electrical shock hazards of this nature.
A GFCI constantly monitors the flow of current through a protected lighting fixture, pump motor, or appliance circuit and senses any loss of current to an outside path. If the current flowing into an electrical appliance or fixture differs by a very small amount from what flows back out, the GFCI instantly interrupts the current flow to prevent a sustained, lethal level of electricity from reaching the consumer. The consumer may feel a painful shock but should be protected from electrocution.
The National Electrical Code (NEC) requires GFCI protection for cord and plug-connected pumps on pools, spas, and hot tubs; 120-volt underwater lighting fixtures; and receptacle outlets in the vicinity of pools, spas, and hot tubs. Today, the code prohibits electrical installations closer than five feet from water and requires GFCI protection for all electrical equipment, including 240-volt equipment located five to 10 feet from the water and for receptacles within a 20-foot perimeter.
Older pools, spas, and hot tubs may not have adequate GFCI protection. In particular, pools older than 30 years may not have GFCI protection on underwater lighting circuits. Because the NEC provision for spas only became effective in 1981, even somewhat newer spas or hot tubs may not be protected.
CPSC urges consumers to have only electricians who are qualified in pool and spa repairs install adequate GFCI protection for all pool, spa, and hot tub electrical equipment and for underwater swimming pool lighting fixtures. Additionally, outdoor outlets that could potentially be used to plug in electrical appliances (e.g., radios, pumps, washers) used near the pool also should be equipped with GFCI protection. Remember to test the GFCI regularly to be assured of continued protection.
Trust our team of state certified electricians to help determine if all your pool equipment is up to code and safe for you and your loved ones. Safe-Way Electric & Solar Co. would be more than happy to assist you! Call Safe-Way Electric & Solar Co. today at (909) 464-9983.
While we don’t install pool pump motors, we do everything else from pool lights, spa lights, circuit breaker boxes, GFI protection, grounding, and bonding.
Facts & Tips
CPSC is aware of more than a dozen electrocutions and a similar number of electrical shock incidents involving circuits around swimming pools between 1997 and 2002. Electrical incidents involving underwater pool lighting were more numerous than those involving any other consumer product used in or around pools, spas, and hot tubs.
The greater danger associated with electrical shock in a swimming pool is that anyone in the pool may be rendered immobile and unable to rescue themselves or to call for help. Drowning becomes a likely outcome, even if the current is not immediately lethal. Bystanders and would-be rescuers risk serious injury if the current flow isn’t stopped before they make contact with a conductive fixture, such as a ladder, or enter the water to try to help a victim.
Going above and beyond is an understatement for what Safe-Way Electric did for me. Glen and Craig were by far the most honest and detailed electricians I've dealt with. They communicated and explained every solution to my problems before going to work and were extremely generous with their prices. These guys take pride in their work and getting the job done right. Their respectful service is what I appreciated the most. Thank you Safe-Way Electric. I don't review much but these guys deserve it. If you are looking for an electrician, definitely look to Safe-Way first.