Understand the Safety Requirements for Wiring Pool, Spa, and Sauna Equipment in California
The U.S. Consumer Product Safety Commission (CPSC) recommends installing and using ground-fault circuit-interrupters (GFCIs) for protection against electrocution hazards involving electrical circuits and underwater lighting circuits in and around pools, spas, and hot tubs.
While grounding provides essential protection for pool, spa, and hot tub equipment, GFCIs are the most effective means for protecting people against electrical shock hazards of this nature.
A GFCI constantly monitors the flow of current through a protected lighting fixture, pump motor, or appliance circuit and senses any loss of current to an outside path. If the current flowing into an electrical appliance or fixture differs by a very small amount from what flows back out, the GFCI instantly interrupts the current flow to prevent a sustained, lethal level of electricity from reaching the consumer. The consumer may feel a painful shock but should be protected from electrocution.
The National Electrical Code (NEC) requires GFCI protection for cord and plug-connected pumps on pools, spas, and hot tubs; 120-volt underwater lighting fixtures; and receptacle outlets in the vicinity of pools, spas, and hot tubs. Today, the code prohibits electrical installations closer than five feet from water and requires GFCI protection for all electrical equipment, including 240-volt equipment located five to 10 feet from the water and for receptacles within a 20-foot perimeter.
Older pools, spas, and hot tubs may not have adequate GFCI protection. In particular, pools older than 30 years may not have GFCI protection on underwater lighting circuits. Because the NEC provision for spas only became effective in 1981, even somewhat newer spas or hot tubs may not be protected.
CPSC urges consumers to have only electricians who are qualified in pool and spa repairs install adequate GFCI protection for all pool, spa, and hot tub electrical equipment and for underwater swimming pool lighting fixtures. Additionally, outdoor outlets that could potentially be used to plug in electrical appliances (e.g., radios, pumps, washers) used near the pool also should be equipped with GFCI protection. Remember to test the GFCI regularly to be assured of continued protection.
Trust our team of state certified electricians to help determine if all your pool equipment is up to code and safe for you and your loved ones. Safe-Way Electric & Solar Co. would be more than happy to assist you! Call Safe-Way Electric & Solar Co. today at (909) 464-9983.
While we don’t install pool pump motors, we do everything else from pool lights, spa lights, circuit breaker boxes, GFI protection, grounding, and bonding.
Facts & Tips
CPSC is aware of more than a dozen electrocutions and a similar number of electrical shock incidents involving circuits around swimming pools between 1997 and 2002. Electrical incidents involving underwater pool lighting were more numerous than those involving any other consumer product used in or around pools, spas, and hot tubs.
The greater danger associated with electrical shock in a swimming pool is that anyone in the pool may be rendered immobile and unable to rescue themselves or to call for help. Drowning becomes a likely outcome, even if the current is not immediately lethal. Bystanders and would-be rescuers risk serious injury if the current flow isn’t stopped before they make contact with a conductive fixture, such as a ladder, or enter the water to try to help a victim.
I called them out to help with some lighting issues. We needed 3 ballasts replaced and about 16 bulbs. All in all I was pleased with the service. I spotted one of their vehicles at Lowes, I called that day and had somebody out to do the work the next day. Our Electrician was Mitchell. He was knowledgeable, professional, and got the job done pretty quick. They aren't the cheapest out there but with this type of work you do get what you pay for.